Everyone is very concerned about how to maintain the swimming pool equipment?
Today, we have a double pool equipment to talk about the issues that everyone is concerned about. The water quality of the pool has a lot to do with daily maintenance. Maintenance includes water quality maintenance and equipment maintenance and maintenance. Today, the pool equipment is shared with the next pool water treatment equipment.
1.Swimming pool cleaning
Open the valve drain on the main drain. Swimming Pool Equipment After the pool water is drained, close the valve on the main drain. Open the valve water supply on the water supply pipe. When the pool water level is higher than the shallowest pool bottom, close the valve on the water supply pipe. Clean the walls of the pool, the bottom of the pool and the gutter (can be cleaned with dilute acid such as oxalic acid). Open the valve on the main drain pipe, and discharge the sewage from the pool from the main drain at the bottom of the pool and discharge it into the municipal drain.
2. Hair brush cleaning
Cleaning conditions: The circulating water pump is in a discontinuous condition. Swimming Pool Equipment Close the valve before and after the pump to prevent backflow. Open the hair dryer and remove and clean the net bucket. Put the net bucket back into the hair dryer and clean/install the waterproof rubber ring. Open the valve before and after the collector. The hair dryer is cleaned once a week.
3. Swimming pool cycle process cleaning
Cleaning conditions: The circulating water pump is in a discontinuous condition. Connect the suction tube and elastic tube to the water. Turn on the circulation pump and use the elastic tube to push the suction head to absorb the dirt.
Be careful: if the suction is not enough, the valve on the main drain pipe can be properly closed and the suction force will increase. When the pump is circulating, the suction force is large, and the cleaning port cannot be opened. During the cleaning process, the triangular tips cannot always get out of the water surface to prevent inhalation of air and pose a hazard to the pump.
4. Sand tank
Initiating conditions: The circulating water pump is in a discontinuous condition, and the gate valves of the return pipe gate valve and the recoil drain pipe are open. Adjust the multiple valves on the sandbox to the “BACKWASH” backflush. Turn on the main circuit power supply of the water pump, turn on the water pump for 3-5 minutes, and check whether the water in the see-through vial is clear when flushing. Turn off the pump after clearing. Adjust the multiple valves on the sand tank to the "FILTER" normal filter.
Be careful: when the pump is running, do not change the multiple valves on the sand tank.
5. Pump body
Check that the pump body should be free from damage, the nameplate is intact, the direction of the water flow in the swimming pool equipment is clear and clear, and the appearance is regular. Fasten the base screws and do anti-rust treatment. Rolling active, no jamming. Keep punctuality on the work area.
The appearance is regular, the nameplate is clear, the components are fastened, and the swimming pool equipment is grounded. The shell is rust-removed and brushed with anti-rust paint. Disassemble the wire connecting piece in the motor terminal box, and measure the insulation resistance between the phase and phase of the motor winding and the ground between the ground and the ground with a 500V megohmmeter to be not less than 0.5MΩ. The three-phase wire and connecting piece in the motor junction box should be firm and tight, no signs of heat and discoloration, and the mark is clear. Keep punctuality on the work area.
7. Trial operation
Close the main power supply and check that the power indication should be normal. Manually rotate the motor shaft and the roll should be active. Jog to determine whether the pump steering is correct, if it is wrong, it should be corrected. The pump operation should be stable, no obvious vibration and abnormal sound, the pressure indication is normal, the current is unbalanced, less than 20%, and the electrical appliances of the control cabinet have no bad noise. Keep a record of maintenance.
Contact Person: Ms. qeenly zeng